This is an official version.
Copyright © 2017: Queens Printer,
Smoke-free Environment Regulations, 2005
Smoke-free Environment Regulations, 2005
Under the authority of section 11 of the Smoke-free Environment Act, 2005 , the Lieutenant-Governor in Council makes the following regulations.
Robert C. Thompson
These regulations may be cited as the Smoke-free Environment Regulations, 2005.
2. In these regulations
(a) "Act" means the Smoke-free Environment Act, 2005 ; and
(b) "independent mechanical ventilation system" means equipment that provides fresh air to and exhausts air from a public place or workplace so that no amount of air that is exhausted from a designated smoking room or a designated e-cigarette use room is permitted to return to a public place or workplace.
3. (1) An employer shall, by posting clearly visible signs, inform all employees in a workplace under the control of the employer
(a) that smoking is prohibited in all work spaces except in designated smoking rooms and designated e-cigarette use rooms; and
(b) of the location of all rooms that are designated smoking rooms and designated e-cigarette use rooms.
(2) Where an employer is in control of a workplace to which the public is admitted, the employer shall, by means of a clearly visible sign posted at each entrance to the workplace used by the public inform members of the public who enter the workplace that smoking is prohibited.
(3) Notwithstanding subsection (2) and section 5 a facility to which subsection 4(2) of the Act applies shall post clearly visible signs stating
(a) that smoking is prohibited except for residents in designated smoking rooms or designated e-cigarette use rooms; and
here by a section of these regulations a sign is required to indicate
(a) no smoking, the sign shall use the graphic no smoking symbol or state "no smoking";
(b) a designated smoking room, the sign shall use the graphic designated smoking room symbol or state "designated smoking room"; and
(c) a designated e-cigarette use room, the sign shall state "designated e-cigarette use room".
(2) Notwithstanding that the symbol described in paragraph (1)(a) includes a cigarette, it shall be considered to refer to the smoking of any tobacco product, vapour product or non-tobacco shish a product.
Public to be informed
5. An owner of a public place shall, by means of clearly visible signs, inform members of the public who enter that public place that smoking is prohibited.
6. (1) A designated smoking room and a designated e-cigarette use room shall have an independent mechanical ventilation system and the employer or owner responsible for that room shall ensure that
(a) the positioning of the intake or exhaust openings provides for the removal of the smoke from the designated smoking room and the designated e-cigarette use room in an effective, efficient manner and prevents smoke movement into adjoining rooms;
(b) the system is maintained and monitored in accordance with the manufacturer’s requirements, but in no case shall the maintenance interval exceed 6 months;
(c) records of maintenance are maintained and available on demand to inspectors designated under the Act and maintenance records shall be kept for a minimum of 2 years;
(d) the volume of air supplied and the rate of exchange of air is determined with consideration to the size and expected occupancy of the designated smoking room and designated e-cigarette use room, subject to the minimum requirements of subsection (2); and
(e) the rate of exchange of air is at least
(i) where the occupancy of the designated smoking room or designated e-cigarette use room is not more than 5 persons and their use of the room is occasional, not less than 6 air changes per hour, and
(ii) where the occupancy of the designated smoking room or designated e-cigarette use room exceeds 5 persons or the room is utilized regularly, not fewer than 10 changes per hour.
(2) The volume of air supplied in a designated smoking room and a designated e-cigarette use room shall be of a flow volume that is not less than 14 litres per second or 29.7 cubic feet per minute of air supplied for each occupant.
Sign and system requirement
7. An employer or owner responsible for a workplace or public place shall ensure that signs and independent mechanical ventilation systems required under these regulations are posted and installed.
8. An event for which a licence has been issued under section 14 of the Liquor Licensing Regulations shall be exempt from the application of the Act and these regulations where that event is not held in a building or other enclosed space.
NLR 54/98 Rep.
The Smoke-free Environment Regulations
10. These regulations come into force on July 1, 2005.